is part of the Informa Markets Division of Informa PLC
This site is operated by a business or businesses owned by Informa PLC and all copyright resides with them. Informa PLC's registered office is 5 Howick Place, London SW1P 1WG. Registered in England and Wales. Number 8860726.
19/04/2022 | Sara Bean, editor, FMJ | An article written exclusively for Facilities Show by FMJ
Like many buildings in the UK, commercial office buildings have been affected by the Covid-19 pandemic, specifically, how often, and how they are used. This blog explores the risks that water poses in these types of buildings and in particular the risk of Legionella bacteria.
Legionella bacteria are common in natural water sources such as rivers and lakes, they may also be found in purpose-built water systems, such as hot and cold-water systems in a commercial office building. It is these types of “man-made” water systems that pose the greater risk to humans, as the conditions for Legionella proliferation and exposure are increased.
Commercial offices are those buildings used by differing types of businesses as a place of work. Standard office spaces are commonly divided into workspaces, kitchens, restrooms, and service rooms such as cleaners’ cupboards and plant rooms.
What is required?
All commercial building operators in the UK have duties under the Health and Safety at Work etc Act 1974 (HSWA) which extends to risks from legionella bacteria, may arise from work activities. As the duty holder in control of a commercial office, you must;
Who is responsible?
Whether you are the landlord/owner or tenant, the actions above must be undertaken, but like many commercial offices, these tasks may be undertaken by different parties. Unless a “fully maintained” lease is in place it is ultimately the responsibility of the landlord or owners to manage the building, this includes the water systems and other Health and Safety risks (including Legionella). If you are a tenant of a building (without a fully maintained lease) and are responsible for your employee’s health and safety, it would be advisable to seek evidence of compliance from your landlord.
In some cases, fully maintained leases exist between landlords and tenants, that transfer responsibility from the landlord to the tenant for some or all the required tasks. In some cases, the tenant may feel they require more control over health and safety matters and undertake the tasks listed above themselves.
Whatever arrangement is in place, records of work carried out to manage Legionella need to be kept up to date and readily available for inspection.
Types of water systems
Commercial office buildings range in size and complexity. It is fair to say, that the larger and more complicated a building and the water system is, the greater risk of Legionella is presented, which in turn, requires more elaborate control methods. The types of water systems found at commercial office buildings include;
Each water or risk system requires a Legionella risk assessment and a resulting control scheme established. A control scheme will include monitoring, inspection, cleaning, and disinfection frequencies, so the more complex a water system is, the more controls they usually require.
One of the more topical issues regarding Legionella in commercial office buildings is water system usage. These types of buildings have experienced different levels of use during the pandemic, ranging from complete shutdown to reduced staffing levels. This impacts the water system as less water is being used daily, thus creating reduced flow, stagnation, and possible biofilm problems. The Legionella Control Association have reported that lockdowns have increased the rate of positive Legionella sample results. So, if your building has seen a different level of use recently, has the Legionella risk assessment been reviewed? Has the amount of stored water been assessed? Have different control measures been implemented?
Scalding – Has a scalding risk assessment been carried out? Unnecessary installations of thermostatic mixing valves (TMV’s), especially in staff areas, can increase the risk of Legionella colonisation due to their complexity and maintenance requirements. The scalding protection should be applicable to the risk.
Hot water boilers – Having replaced the traditional kettle, these installations can affect how much the sink taps are used. If drinking water dispensers are also used, is the sink cold tap being used at all? If a dishwasher is present, what are you using the hot tap for? The use of all outlets requires regular review.
Drinking water dispensers – as mentioned above, these have replaced the humble cold-water tap, decreasing their use. If desired, mains-fed units are preferred to bottle-fed types, due to the quality of water supply, maintenance, and cleaning practicalities. If installed, mains-fed units should be sited as close as possible to a regularly used outlet to assist-turnover.
As with any commercial premises and health and safety matters, the starting point is always risk assessment. This will inform the landlord or building owner of any gaps in Legionella and water hygiene management and help form a plan to actively manage any Legionella risks identified.
CHARLIE BRAIN IS A SENIOR CONSULTANT, AT WATER HYGIENE CENTRE LTD